Connect BACnet MS/TP Devices to a Profibus Controller
The 460BMPBS moves data between up to 32 BACnet MS/TP devices and a Profibus DP Controller. It’s the perfect tool to tie all the BACnet MS/TP devices in your automation system to Profibus.
How Do I Use 460BMPBS-N70PB in My Application?
BACnet MS/TP data will be mapped into 10 Profibus DP slots. Each Slot will be assigned a typed of Int8, int16, int32, int64, Uint8, Uint16, Uint32, Uint64, float, double, binary8, binary16, or binary32. The Slot can consist of up to 244 bytes of data from your BACnet MS/TP devices.
When writing from your Profibus Controller to your BACnet MS/TP devices, there will be up to 10 Slots each defined by the same type. Data in those slots can be mapped to your BACnet MS/TP devices.
Why use Real Time Automation as a Gateway Supplier?
While there are certainly other companies offering protocol gateways, there is no one who provides the level of support and service that you receive from RTA.
When you call, a live person answers the phone. When you talk with sales, you will get honest answers and recommendations. When you get support, it is from an engineer who had a hand in the product’s development, and support doesn’t require a ticket or 24-hour wait.
Try the RTA difference today.
BACnet MS/TP Master Features
BACnet/ MS/TP Operation Modes
BACnet MS/TP Master Initiator
Supported Object Types
Device, Binary, Analog, Multi-State, Character String Value
Supported Service Codes
Read Property-A, Read Property Multiple-A, Write Property-A, Write Property
Multiple-A, Device Dynamic Binding-A
Number Read/Write Scan Lines per Device
200 Total - 100 reads & 100 writes
Scan Line Support
Up to 128 Total Objects
Profibus Slave Features
10 Slots in each direction
2, 4, 8, 16, 24, 32 Bytes
int8, int16, int32, int64, uint8, uint16, uint32, uint64, Float, Double, binary8, binary 16, binary 32, Short String
Total Data Supported
244 Bytes in each direction
Maximum Profibus DP Connections
You can configure up to 9 different users access to diagnostic and configuration screens.
Set <, <=, >=, >, ==, !=, and Change-of-State rules on any data moving through the gateway. If alarm rule is triggered an email notification can be sent.
Allows for data manipulation during protocol translation. Scaling and other data format changes can occur in the gateway.
Status and Counters
Protocol specific status, counters and error messages are accessible within the gateways diagnostics page. They can also be delivered to a connected device.
Diagnostic Logging Page
Allows users to see and log start up sequences, protocol specific messages & error messages.
to download our Gateway Comparison PDF